gas fired hot water boiler for paper mill
Operation of the boiler, including what? Including the operation of the boiler, what does? Following on from the Henan fast boiler company to tell you about: 1. The water level regulation of normal water level in the middle of the gauge (1) of the boiler. Operation with the magnitude of the load is adjusted: to maintain a high level during low load, high load to maintain a low level. Changes should not be down more than 40 mm. (2) to be run on the water level gauge to compare the two groups, if the water level display should be corrected promptly identify the cause. (3) To achieve a balanced continuous boiler feed water, ground water supply, water supply less, to maintain the water level in the normal water level fluctuates slightly in the vicinity. (4) load change is large, prone to false level. Pay attention to judgment, in order to avoid misuse. 2. Steam pressure regulator (1) when the boiler must constantly monitor the pressure gauge indicated. To maintain stable steam pressure, boiler pressure must not exceed the design pressure. (2) increasing the boiler load: Steam pressure decreased boiler load is increased, if the level is high at this time, the amount of water should be reduced to a water supply or suspend, the amount of coal and increase the air volume. Gradually increase the amount of water at the same time to strengthen the burning, keep the steam pressure and the water level is normal. (3) boiler load reduction: the vapor pressure rises to reduce boiler load, if the level is high at this time, the amount of coal should be reduced and the air volume, reduced combustion. Then the appropriate water reduction or suspension of water supply to the water vapor pressure and stability in the nominal range. Then press the normal combustion and to adjust the amount of water. If the actual water level within the boiler is low, to increase the amount of water should, until the water level returns to normal after the combustion and needs to be adjusted according to the water vapor pressure and load changes. 3. Combustion adjustment (1) combustion index. Normal combustion boiler comprises a uniform supply of the fuel, reasonable ventilation, adjusting three basic aspects combustion. B. maintain a high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100-1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. C. fuel ash to reduce ash content in the combustibles to be below 10%. d. reducing the temperature of the exhaust gas boiler exhaust gas temperature should be controlled below 200 ℃. e. excess air negative pressure holding furnace boiler 1.2-1.4, by adjusting the balance of the blowers to maintain the furnace pressure is 2-3mm. F. to improve the thermal efficiency of the boiler thermal efficiency of the boiler should be kept above 60%. (2) adjusting the combustion a. Reasonable amount and the distribution of fuel to the amount of air needed for combustion. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. b wind principle feature: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. c is the normal combustion conditions: fuel ignition start at 300mm from the shutter of coal, even flames, the fire bed formation, at the end away from the combustion grate at the end of 300-500mm. d. Hold appropriate furnace temperature to avoid coking. E. fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. F. less than 30 minutes residence time of the fuel on the grate. Our company provides services related to the installation of the boiler!
General food factories are large in scale and the factory area will be built in industrial areas. In this way, the application of the boiler is required for the heating of the plant and the supply of hot water. The oil and gas boilers produced by ZG boiler have heating boilers and hot water supply boilers, which can heat the food factory, dormitory, office building, and provide domestic hot water such as bath water.
Gas boiler which has few parts of the main gas boiler: the enclosed pipe chimney pipe tube sheet base gas outlet steam dryer Confining the majority of the peripheral tubes to form a complete gas boiler. The main effect of gas boiler: the combustion of the fuel is heated by the feedwater temperature and the exothermic heat of the flue gas with a heated surface, so that a final water into superheated steam having a quality of qualified certain parameters. The water in the boiler to go through preheating, evaporation, overheating in three stages in order to become superheated steam. In fact, in order to improve the efficiency of the steam power cycle, there is a fourth stage, i.e. re-superheating stage, soon after the high pressure turbine expansion work to reduce the pressure and temperature of the steam back to the boiler is heated and then sent to the low pressure turbine cylinder continues to work. In order to meet these four phases change, the boiler must be arranged in the respective heating surface, i.e. the economizer, water wall, superheater and reheater. Superheater and reheater disposed in an upper horizontal flue backpass and functions of the fuel system is to ensure the desired fuel burner. The fuel oil burner system are: tubing and fittings, pumps, solenoid valves, nozzles, heavy oil preheater. The gas burner mainly a filter, pressure regulator, solenoid valve, and then firing solenoid valve, the fuel valve. Economizer disposed in the lower back pass. In order to utilize flue gas heat of heated air required for combustion, usually air preheater arranged after the economizer. Some additional preheating large boiler superheater heating surface or in the furnace, and then heat-receiving surface.
Fast boiler has always "shaping the character, and create boutique" business philosophy, focusing on clean fuel boiler design and development, has won much praise. Not forgetting beginning of the heart, was always square. Fang help Qiaqia fast food, the taste of happiness with the power of innovation.