cfb commercial boiler prices
Six reasons to explore the burner gas cfb commercial boiler prices is not operating
1, the gas pressure is lower than the low voltage protection switch. On Check gas valves are open, if there is gas in the tank.
2, the gas pressure is higher than the pressure protection switch. Shut off valve, and check the pressure reducing valve or regulator box has failed.
3, steam boiler water level is too low, there is very low interlock. Boiler water level observation, grasp the true level, after manual Sheung Shui to eliminate problems.
4, gas steam boiler pressure is higher than the starting pressure. Natural gas and other boiler pressure to reduce the pressure to start, you can start properly.
Central heating hot water cfb commercial boiler pricess for heating in winter is an important measure in most parts of China. Hebei Guan China Fortune Foundation Limited mainly engaged in real estate projects, is a leading industrial town operators. Heating service is primarily aimed at the Group's residential housing and other real estate. With the full open sky Battle, continue to improve the proportion of clean heating, heating for the implementation of clean energy, China Fortune Foundation to purchase much-needed high performance hot water boiler clean and green products. After comparing a number of boiler plants, the best of the best, determined to cooperate with the fast boiler in abundant clean energy R & D experience in boiler party. Providing fast boiler SZS Series 2 gas hot water boiler according to the actual needs, respectively 58MW and 29MW.
Pay attention to gas steam cfb commercial boiler prices which runs: customer after purchasing gas steam boiler, not sit back and relax, but also need to seriously understand the operation of the boiler starts, the attention to what matters, so you can be more effective in ensuring the long life of the boiler. 1, the cold gas steam boiler working pressure from the ignition rises, boost heating time is about 3 to 4 hours. When the boiler pressure rose to 0.05 ~ 0.1MPa, should wash boiler pressure gauge and water level gauge; when the boiler pressure rose to 0.15 ~ 0.2MPa, the boiler should be shut down air valve and check valve for leaks, measures should be taken if a leak be eliminated; when the boiler pressure rose to 0.2 ~ 0.25MPa, boiler blowdown to conduct a test, when sewage boiler water level should be above the normal water level, and check the drain valve leaks, if the leak should take measures to eliminate; when the boiler when the pressure is raised 0.3MPa, a full review of the fastening member boiler pressure element, such as manholes, hand bolt holes, and check holes of each flange connection is loose, and a tighten heat. 2, the pump checks whether the automatic operation to maintain the normal water level, water level in the "line from the pump" the normal start, the water level in the "stop pump line" pump can be stopped; 3, control pressure is normal, when the steam pressure reaches when the set value, the combustion is stopped, lights overpressure, the pressure is reduced to the set value, the boiler can start automatically; 4, when the load pressure reaches the set value, the fire load due to a small fire, when the pressure drops to set when the predetermined value, the transfer of small fires burning fire; 5, when the pressure can not be set at normal pressure shutdown, the shutdown will alarm the second overpressure shall be restarted; 6, the exhaust gas temperature should not exceed 300 ℃, otherwise, the shutdown should check; 7, when gas steam boiler into normal operation phase, boiler fireman personnel to strengthen the boiler, instrumentation and safety accessories and auxiliary equipment is a monitor, a good job is a boiler and auxiliary equipment inspection tour and in a timely manner fill run record.
The quality of natural gas cfb commercial boiler pricess also have a strong relationship with the device operating parameters and presets. If the operator of the gas-fired equipment to adjust each parameter does not match with the environment, or confusing sequence of operations may also lead to natural gas boilers in the course of the system Caton, excessive condensation water, low pressure or no change in temperature abnormal situation. Therefore, the relevant personnel to operate natural gas boiler must be in accordance with the instruction proper operation boiler, preferably with professional instructors and auxiliary operations. Third, the repair and maintenance of gas boilers