combined 0 5 Ton condensing boiler Dealer
First, what is condensing combined 0 5 ton condensing boiler dealer
More energy-efficient condensing boiler is a special equipment to save money, according to their capacity needs of different industries, ranging from 0.5 to 20 tons; compared with the traditional boiler with high thermal efficiency, safety, noise, environmental protection, pollution-free advantages.
Essential fuel combustion will produce a large number of CO2, NOX and SO2 and other substances, these substances emitted into the atmosphere, cause the greenhouse effect and acid rain, have serious damaging effects on the environment. Condensation combined 0 5 ton condensing boiler dealer flue gas while condensing water vapor, the flue gas can be removed in these harmful substances. Therefore, the use of condensing boilers is also important to protect the environment.
Autumn and winter cold season is heating the peak of the northern city of Tianjin, with the heating period, fog, haze and other inclement weather has cropped up, as also the people a "blue sky" always in a good living environment, inside of Tianjin low-emission coal-fired combined 0 5 ton condensing boiler dealers reform process without delay. To improve the situation of air pollution, Tianjin start the "Blue Sky Project" plans to cooperate with the fast boiler, gas boiler will invest billions of dollars in coal-fired boilers within the city as a clean fuel such as natural gas as raw material.
After the pipeline pressure test of the combined 0 5 ton condensing boiler dealer boilers, valves, meters and other installation, cleaning up outside the boiler, close the manhole, hand hole, then pressure test in accordance with the relevant provisions of the "Steam Boiler Safety Technology Supervision" of. Specific test as follows: 1, should be ready before the hydrostatic test the following: (1) for internal cleaning and inspection of the surface of the test portion. (2) Check the clogging of the tubes. (3) mounted to verify compliance with the pressure gauge (not less than 2). (4) mounted good deflation valve and drain line. 2, the hydrostatic test shall meet the following requirements: (1) hydrostatic test shall be carried out when the ambient temperature is higher than 5 ℃, or should be protected from freezing, temperature should be higher than the ambient water pressure dew point temperature, generally 20 to 70 ℃. (2) when the water pressure up to the working pressure should be temporarily stopped a boost, check the various parts for leaks, and then rose to the test pressure for 20 minutes after the pressure back down to work, to be checked. During the inspection the pressure should remain unchanged. 3, meet the following criteria to be acceptable: (1) no water mist on the pressure-receiving element and the metal wall and welds. (2) Expansion mouth bead does not drip down when the operating pressure. (3) pressure test, no residual deformation. These are the work of the boiler pressure test can help you better understand the boiler equipment, hope this can be helpful to you in the future use.