high effective gas fired boiler
3. Adopt flue gas return body coil design, this DC-type structure, show the traditional high effective fired boiler does not have security.
4. As a result of coil-type structure and therefore, sufficient heating surface so that it will have a higher thermal efficiency.
5. Heat-conductive of boiler, characterized by significant counter-current heat exchanger, combustion exhaust gas temperature and thermal conductivity of the oil exports of the following temperature at 30C.
Gas-fired steam high effective fired boiler safety valve from installation to use, it must remain vigilant safety valve is one of the most important components of the gas steam boilers, boiler probability of the risk occurring due to various incidents can effectively suppressed. This article focuses on the safety valve from installation to use several important considerations, we do not ignore the use of gas when it steam boiler. A Notes 1 safety valve, the safety valve should be mounted vertically in a high position in the pot business, set box. 2, between the safety valve and the drum or header, not equipped with access to the steam outlet pipe and the valve. 3, the lever-type safety valve should prevent movement of the self-apparatus and the weight limit leverage deviant guide tube, a spring safety valve should lift and handle means for preventing movement of the adjustment screw is screwed lightly. 4, the rated steam pressure less than or equal to 3.82MPa gas steam boiler safety valve throat diameter of not less than 25mm; power greater than the rated steam pressure 3.82MPa boiler safety valve throat diameter not less than 20mm. 5, the safety valve and coal-fired steam boiler tubes, the cross-sectional area not less than the cross-sectional area of the valve inlet. If several valves installed together with a short tube directly connected to the drum, the cross-sectional area of the passage should not step short tube to 1.25 times the area of all the exhaust valve. 6, the safety valve should normally be installed exhaust pipe, exhaust pipe should be through a safe place, and there is sufficient cross-sectional area to ensure the smooth flow of exhaust. 7, the safety valve exhaust pipe at the bottom should have received a place of safety posturing of drainage pipe, the exhaust pipe and drainage pipe not allow the installation of the valve. 8, rated evaporation to 0.5t h coal-fired steam boiler /, at least two safety valves installed; Rated evaporation 0.5t h less than or equal to electric boiler /, mounted on at least a safety valve. 9, separable economizer outlet, the steam superheater outlet valve must be installed.
Industrial gas steam high effective fired boiler for industrial use industrial gas steam boiler is a low-pressure gas steam boiler, but its high thermal conductivity temperature of the liquid inside, and the liquid explosive is mostly, if working in industrial gas steam boiler thrown thermally conductive fluid leak and cause a fire or even a large possibility of an explosion, which is very dangerous, so run industrial gas steam boiler safety is often worth the length of the face. Because the range of high temperatures (above 320 ℃), low voltage (0.3 to 0.5MPa), the heating temperature can be precisely controlled, it can replace the original steam boiler heating. Industrial gas steam boiler is heated up to a temperature of 350 ℃, molten salt furnace is heated up to a temperature of 530 ℃. Because the ash can not be produced by industrial combustion gas steam boiler fuel gas, if the gas and air mixture into the furnace is injected within a certain range may explode. Gas steam boiler operating temperatures above 400 ℃ oil and molten salt heat transfer medium, having a molten salt heat steam than the gas lifetime advantages, but otherwise are at a significant disadvantage, in particular the complexity of running the system.
The fact that we determined to achieve cooperation with the fast high effective fired boiler is a very wise decision, after a period of time put into the boiler efficiency significantly much higher than our original boiler efficiency, significantly reduce fuel costs, the economic benefits brought by the boiler is obvious. --customer feedback