sime combi boiler manual
Fast sime combi boiler manual strong technical team and perfect after-sales service to our left a deep impression, the successful completion of the boiler installation and commissioning work at a predetermined period. The company offered me two Taipower heating steam boilers, combined with the actual situation of our company, as we save a lot of fuel costs, thanks to fast boiler provides us with such high-quality products and peace of mind. --customer feedback
How are pressure hot water sime combi boiler manual plant is not a professional formal professional regular pressure hot water boiler plant can provide experienced to the public, we targeted one-design, and can provide a more professional and authoritative confined to the public hot water boiler system overall planning, we can ensure that the corresponding boiler industry's top standards, may have the ultra-high-cost, so that everyone can afford to buy there is no money for performance and security with in terms of absolute to achieve the most authoritative eligibility criteria.
Former Chenzhou steam sime combi boiler manual installer to install steam boilers, should write "to start installing the application report", carrying at least including the boiler management authority for all of the following information to the steam boiler earthly boiler installation approval process, before it can start after approval: ① steam boiler installation of the original license; ② steam boiler installation application starts report and installation program; ③ steam boiler certificate material; ④ steam boiler room layout drawings and plane steam boiler room planning material; ⑤ installation company vocational certificate construction workers. Former steam boiler installation, the installation company should also carry approved "to start installing the application report" to everyone earthly quality technical inspection authority Steam Boiler and Pressure Vessel Inspection Branch signed the "quality of the installation agreement responsibility" by the laboratory steam boilers the quality of the installation is completed supervision.
Installation of fuel gas-fired sime combi boiler manual safety valve safety valve is one of the important requirements of the protection device fuel gas-fired boiler, boiler user is necessary for proper installation of the safety valve. Following small talk to the fuel gas boiler safety valve installation points: (1) greater than the rated 0.5t h fuel gas boiler / evaporator, at least two safety valves installed; equal to or less than the rated evaporation 0.5t / h fuel gas-fired boiler, at least install a safety valve. The separable exit of the economizer, steam superheater outlet of the safety valve must be installed. (2) safety valve should be mounted vertically at the highest position boiler drum, collection tank. Between the valve and the drum or header, not equipped with access to the steam outlet pipe and the valve. (3) have lever-type safety valve means for preventing movement of the self-weight and deviant restriction lever guides the spring loaded safety valve should lift and handle means for preventing movement of the adjustment screw is screwed lightly. (4) The rated steam pressure less than or equal to 3.82MPa boiler safety valve throat diameter of not less than 25mm; the rated steam pressure is greater than 3.82MPa boiler safety valve throat diameter of not less than 20mm. (5) safety valve boiler tubes, which cross-sectional area not less than the cross-sectional area of the valve inlet. If several valves installed together with a short tube directly connected to the drum, short tube passage area not less than 1.25 times the area of all the exhaust valve. (6) safety valve should normally be installed exhaust pipe, exhaust pipe should be through a safe place, and there is sufficient cross-sectional area to ensure the smooth flow of exhaust. Safety valve exhaust pipe at the bottom should be fitted to the safe location of drainage pipe, the exhaust pipe and drainage pipe not allow the installation of the valve.