flame smoke tube industrial gas boiler
Combustion conditions provides rapid and substantially complete combustion of 1, a relatively high furnace temperature: the chemical reaction is the basic condition of combustion, fuel ignition and stable combustion, burn have a significant impact, maintaining a suitably high temperature furnace to important. Of course, when the furnace temperature is too high, consider the problem of slagging flame smoke tube industrial boilers. 2, the air supply amount: the amount of air supply, is to provide enough oxygen for the fuel, which is the original conditions of the combustion reaction. Air supply, fuel not get enough oxygen, it can not achieve complete combustion. But excessive air, the furnace temperature will lead to loss and exhaust loss increases. 3, good mixing conditions: Mixing is an important physical conditions of the combustion reaction. Mixing the hot flue gas in the furnace is heated to reflux of the pulverized coal flow, so as to rapidly fire. Mixing in the furnace is strongly perturbed stream to provide oxygen to the soot combustion stage surface, outward diffusion of carbon dioxide, and to promote post-combustion of the fuel burn, it is an indispensable condition. 4, enough burn time: the fuel in the furnace for a time sufficient to achieve a high degree of fuel burn, which requires a large enough volume of the furnace. Proportional to the volume of the furnace and boiler capacity. Of course, the furnace volume is also characteristics of the fuel combustion, easy to burn fuel, furnace volume can be relatively small. For example, the same capacity of the boiler, furnace volume of fuel than pulverized coal furnace is small, and vanished without burning furnace volume than coal burning bituminous coal furnace volume slightly larger.
Recently, Henan Province Industry and Information Technology Commission issued a public list on the Internet in 2018, Henan Province, manufacturing and integration of the development of pilot demonstration enterprises. Provincial and municipal levels of government through a rigorous screening, layers of review, the company flame smoke tube industrial boiler remote monitoring cloud services platform project as a key project in Anyang City was selected. Meanwhile, the provincial Industry and Information Technology Committee recommended that recommendation to declare: "The 2018 National Manufacturing and Internet convergence pilot and demonstration units."
Gas oil furnace gauge acceptance and prohibit the use of instructions for conducting oil furnace oil furnace gas this kind, since both sites flame smoke tube industrial boiler products, is one of the sites keywords, therefore, requires a comprehensive knowledge and understanding. Moreover, it is also a common oil furnace type. Therefore, only familiar with this kind of boiler, we have the right to use, so a lot of benefit to themselves. 1. Gas oil furnace acceptance for this kind of a gas oil furnace oil furnace, which work in the acceptance, the main, are: First, when a gas oil furnace transported to the installation site, the manufacturer should be based on factory inventory, an inventory of its parts, whether there are missing and so on. Then, according to the boiler drawings, review of equipment, mainly to check its associated integrity. For example, the large boiler, during transportation, whether there is damage or deformation such problems. 2. Gas oil furnace gas pipeline for oil furnace installation, in which the pipeline installation, requirements mainly refer to "Heat Transfer Fluid heaters Safety Supervision" in, and should refer to product specifications, as well as the process of FIG. to carry out. For the line connection port, in addition to the flange on the connection should be used to this kind of welding. In addition, the pipeline arrangement, there should be a slope, typically from 2% to 3%. In the high line, an exhaust port shall be provided, at its low due outfall. For straight line pipe, if the length is more than 20m, then there should be a thermal expansion joint. 3. conducting oil furnace gas gauge, when the circumstances under which can not be used? In the gas oil furnace, pressure gauge is an important instrument, but if some situation, then can not continue to use its specific terms, it is as follows: Case 1: broken glass on the pressure gauge, or its dial scale is unclear, unrecognizable. Case 2: Pressure gauge seal is damaged, or it exceeds the test period. Three cases: for a limited gauge nail stop, if there is no pressure, the pointer can not limiting, the staple at the back. If the nail is not limiting, pressure gauge, in the absence of pressure, which is the distance between the pointer and the zero position, more than a predetermined allowable error range.
6 tons adjusting a combustion gas steam flame smoke tube industrial boiler, normal combustion boiler three basic aspects of indicators include a uniform supply of the fuel, reasonable ventilation, adjustment the combustion. 1, to maintain the high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100 ~ 1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. 2, fuel ash to reduce ash content in the combustibles to be below 10%. 3, reducing the temperature of the boiler flue gas exhaust gas temperature should be controlled below 200 ℃. 4, holding furnace negative excess air boiler is 1.2 to 1.4, by adjusting the balance of the blowers to maintain the furnace pressure is -20 ~ -30Pa. 5, the thermal efficiency of the boiler to improve the thermal efficiency of the boiler should be kept above 60%. II. Combustion Adjustment 1, the amount of fuel to air required for combustion and the amount of a reasonable distribution. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. 2, the thickness of the seam and seam thickness configuration grate speed is 80 ~ 120mm grate speed at high, middle and low profile configuration of several commonly used methods:. 9a rapid combustion of thin seam b c thick seam in low combustion. 3 thick seam combustion speed, the segment with the wind blowing principle: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. Normal combustion conditions are: fuel from the coal at the beginning of the fire shutter 300mm, uniform flames, the fire bed formation, at the end of combustion from the end of the grate 300 ~ 500mm. 4. maintain proper furnace temperature to avoid coking. The fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. 6. The residence time of the fuel on the grate in less than 30 minutes.