gas boiler of low consumption
How many calories Horizontal one ton steam boiler of low consumption needs? 1 ton steam boiler, require 600,000 calories, biomass is the most economical fuel. 1 t of steam boilers, 600,000 calories needed, is converted into fuels: diesel 58kg / hour, i.e. cost of diesel and 466 / hour; biomass particles 150kg / hour, the cost of 165 / hour. 697 electrical degrees / hour, i.e. cost of electricity 697 / hour; gas 75m3 / hour, i.e. cost of natural gas 375 / hour; 120kg of coal / hour, i.e. cost of coal is about $ 120. As can be seen from the above, coal and biomass particles are the most economical. Wherein the combustion of coal is difficult to control, and the actual consumption costs considerably biomass particles. However, polluting coal boiler is very large, and the biomass boiler is both economical, and environmentally friendly. Accordingly, we can see that biomass pellet boiler is the best future direction of development of the industry boiler, the boiler will also become the industry mainstream.
6 tons adjusting a combustion gas steam boiler of low consumption, normal combustion boiler three basic aspects of indicators include a uniform supply of the fuel, reasonable ventilation, adjustment the combustion. 1, to maintain the high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100 ~ 1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. 2, fuel ash to reduce ash content in the combustibles to be below 10%. 3, reducing the temperature of the boiler flue gas exhaust gas temperature should be controlled below 200 ℃. 4, holding furnace negative excess air boiler is 1.2 to 1.4, by adjusting the balance of the blowers to maintain the furnace pressure is -20 ~ -30Pa. 5, the thermal efficiency of the boiler to improve the thermal efficiency of the boiler should be kept above 60%. II. Combustion Adjustment 1, the amount of fuel to air required for combustion and the amount of a reasonable distribution. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. 2, the thickness of the seam and seam thickness configuration grate speed is 80 ~ 120mm grate speed at high, middle and low profile configuration of several commonly used methods:. 9a rapid combustion of thin seam b c thick seam in low combustion. 3 thick seam combustion speed, the segment with the wind blowing principle: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. Normal combustion conditions are: fuel from the coal at the beginning of the fire shutter 300mm, uniform flames, the fire bed formation, at the end of combustion from the end of the grate 300 ~ 500mm. 4. maintain proper furnace temperature to avoid coking. The fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. 6. The residence time of the fuel on the grate in less than 30 minutes.
Pushing new fast boiler of low consumption - a low nitrogen vacuum boiler "APH the T7" heavy starting at the show, numerous suction eye. "Thalia T7" launch, breaking the old burners + furnace construction mode, rational arrangement of low nitrogen burners, coupled with the furnace scientific, greatly enhance the operational efficiency of the boiler, the real "coupled," "burning "Tiancheng.
WNS oil gas fired horizontal steam boiler of low consumption
Trust The horizontal boiler Experts at ZG Boiler