srilanka boiler kukul parm
Core condensing srilanka boiler kukul parm technology: condensing boiler technology core of low nitrogen premix combustion technology: metal fiber premix burner is a low nitrogen gas and the air proportion is completely mixed prior to entering the combustion chamber, combustion of natural gas, while reducing the air demand, increase the dew point of the flue gas, the flue gas is condensed into the early stage, in order to further improve the combustion efficiency; while reducing the flame temperature to reduce generation of NOx, the NOx emission at the lowest operating conditions can be controlled to below 40ppm.
The only example of an ultra-low nitrogen oxide emissions through srilanka boiler kukul parms Enterprise Test - fast boiler, the production of gas hot water boiler, gas steam boiler, condensing boiler integrated, NOx emissions is far below the required standards, environmental protection departments successfully passed the test and get the user's praise.
Boiler room during the vertical coal-fired steam srilanka boiler kukul parm are not allowed to lock or bolted Vertical coal-fired steam boiler room and boiler load-bearing beams and other components should be a certain distance or take other measures to prevent the high temperature damage. Vertical coal-fired steam boiler having at least two outlets each respectively provided on both sides. Vertical fired steam boiler total width of the front end does not exceed 12m, and the area not exceeding 200 square meters single boiler can be only one outlet opening. Vertical coal-fired steam boiler room leading to the outside doors should open outwards, are not allowed to lock or bolted during operation of coal-fired vertical steam boiler. Door Vertical coal-fired steam boiler-room studio living room or boiler room should be open. Vertical coal-fired steam boiler room and entrance channel should be smooth. Vertical coal-fired boiler apparatus is arranged to be easy to operate a steam room, and service access. Vertical coal-fired steam boiler room should have adequate lighting and good ventilation and the necessary cooling and freezing measures. Vertical coal-fired steam boiler room should prevent accumulation of water. Vertical coal-fired steam boiler room floor should be smooth and no steps.
Boiler excess air ratio is too low or too high, what harm? What causes high excess air ratio is? A: The srilanka boiler kukul parm excess air ratio is one of the important characteristics of operational quality, the size value shows the degree of perfection combustion equipment and boiler operation. Excess air ratio is too low, incomplete combustion, increased flue gas of CO, the thermal efficiency is reduced; the excess air ratio is too high, the cold air does not participate in the combustion reaction in a large amount into the furnace, furnace temperature to drop, complete combustion. Also part of this excess of air also absorbs heat warming, and to take away the heat with the flue gas, reducing the thermal efficiency of the boiler. Therefore, a reasonable excess air ratio should not only ensure complete combustion of the fuel, but also can minimize the heat loss. Many cities now used in the boilers, a high excess air ratio, is because: (1) mechanical ventilation mismatches, to the excessive wind; (2) a furnace body, door, etc. leakage; (3) a flue, purification device air leakage.