boiler for individual heating stations
To ensure the safety of special equipment such as boiler for individual heating stationss, in normal use, to further promote the comprehensive management of environmental pollution, since April this year, Khorgas Market Supervision Administration of Quality Supervision Bureau for the joint Yili area within the jurisdiction of Khorgas , launched a special safety inspection activities boilers.
Law enforcement officers to be included within the jurisdiction of the major hazard of 12 boiler units of a total of 21 boilers individually conduct a special inspection, focus on examination of the "three implementation, two certified, a test, a plan," the implementation of a detailed view of boiler safety management system, run records.
Test results showed that most of the boiler unit security management more standardized, but there are still some units use boilers run records were incomplete, part of the boiler has to inspection cycle, has been scrapped or dismantled boiler is not write-off and other issues, law enforcement officers to issue on-site boiler sealed, and ordered boiler unit for rectification.
Gas central heating boiler for individual heating stations deactivated after the release came out of water, the pot or the furnace very humid, coupled with insufficient ventilation, long time in a wet state. After a lot of air to enter all parts of the air involved are likely to produce oxygen corrosion, and erosion due to ulcer type and form of multi-spot-based corrosion, resulting in a lot of rust. This effect will be that the internal boiler corrosion metal wall thinning, reduced strength, shortening the life of the gas central heating boiler.
When we use a gas-fired boiler for individual heating stations, we first open the burner door, remove the rear housing panel, and unscrew the rear side cleaning port of the boiler. Clean the gas pipeline with a steel wire brush. Clean the combustion chamber with a soft brush. Gas-fired boiler remove residue from the boiler, screw the clean port, close the burner door, and check that the sealing ring is intact. If the boiler is installed in an area where the temperature is below 0 ℃, the following protective measures must be taken: if the boiler room is outdoors, the indoor temperature shall be lowered to 15 ℃ or 18 ℃, so that the boiler can operate throughout the day. If there is no one in the room for a long time, the water in the boiler should be emptied.
Industrial boiler for individual heating stationss defects approach to industrial boiler defects approach based on "Boiler Safety Technology Supervisory Regulations" TSGG0001-2012 first article 184.108.40.206, the boiler should be carried out major repairs. Installation and repair should be qualified in accordance with relevant technical units standards and technical regulations, but no pressure element replacement requires less than the required boiler design and manufacture. According to "Rules Rules chemical cleaning boilers" TSGG5003-2010, perform the chemical cleaning boiler cleaning. Industrial boilers defect prevention measures using the unit managers, workers should enhance learning and strict implementation of the safety management system boilers, boiler water (medium) quality management system; to ensure reliable operation of water treatment systems, boiler feed water quality assurance; conditions can be the establishment of boiler water quality laboratory, real-time monitoring of water quality boiler operation, there is growth targeted control of scale.