lp steam boiler capacity 150td
State all the more attention to environmental protection, to provide more excellent atmosphere, we respond positively to the country's environmental protection, promote the boiler from coal to gas project. Among the many boiler suppliers, we chose the fast boiler. First, the party quickly done very well in terms of cleaning the boiler, the second is fast side also very comprehensive after-sales involved. The optional gas boiler was used after running fully meet the needs of our pharmaceutical production, both energy-saving and environmental protection, but also a very high thermal efficiency, saved us a lot of fuel costs. --customer feedback
Rinsing step boiler water level gauge for boiler water level gauge flushing clean water level gauge mica or glass, to prevent clogging of the steam or water communicating tube, to prevent erroneous determination caused by operating personnel accident level. The step of rinsing water level gauge as follows: (l) soft drinks first side of the secondary door is closed, to open 1/4 ~ 1/3 times, and then open the door turn on the water, and washing soda mica conduit. (2) stripping off water measured secondary-side doors and mica flushing conduit. (3) off the water of the secondary side of the door, the second door ajar steam side, the steam side and the mica sheet for rinsing. (4) micro-water side of the secondary door, turn on the water shut the door, the water level should rise quickly, and fluctuates slightly, indicating clear, or should be washed once again. (5) The secondary side soda doors open, and the other with control water level gauge, indicating consistent. (6) should not be too long time rinsing water level gauge, and the protection level gauge pin to prevent clogging.
Multiple parallel lp steam boiler capacity 150tds, if a boiler is not operating at full load state, whether the pressure of the boiler can reach the set value? Causes the pressure in the boiler, because the water in the boiler to absorb heat from the liquid state to a gaseous state, its volume expands, and the drum is a closed container, the steam can not be freely expanded, forced compression in the boiler, thus creating pressure. As the boiler is not operating at full load state, by enhancing combustion, can still pressure reaches the set value.
2. Steam boiler in hospitals
Healthcare facilities are generally intensive energy users compared with many other buildings, because of their specialized requirements for 24-hour working. Steam is used widely in many hospitals to provide hot water, space heating and sterilization services. There are good reasons for this. Steam is an efficient and controllable heating medium that is proven to be reliable, safe, flexible and sterile.