500kw hot water boiler oil fired
SZS series oil and gas boiler are D-type quick-assembled water tube boilers. The fuel can be natural gas, light oil, heavy oil, coke oven gas, clean burning, and the water tube boiler have many advangtages that is the easy operation and easy installation.
How to maintain the boiler during operation of the boiler during operation how to maintain water supply and water quality monitoring furnace boiler feed water and boiler water boiler maintenance ⑴ should be consistent with GB / T1576-2008 "industrial boiler water quality" standards. And regularly sampled for testing. The number and frequency of emissions is determined by laboratory personnel. Laboratory and sewage should be detailed records. ⑵ mechanical rotation monitoring for pumps, fans, pumps, etc. to be employed a method of three touch see two monitors. Abnormal phenomenon, that approach to take. If necessary, to shutdown maintenance, are not the effect. ⑶ daily oil tank oil level monitoring if no automatic control device, the oil level should be checked regularly and found that the oil level is too low, the use of two hours is not enough, please notify the staff in advance of the fuel injected new fuel. ⑷ soft water tanks commonly used to control the operating state of the automatic control device ⑸ To periodically check the water treatment apparatus to the ion exchanger is failed, or periodically backwashed. ⑹ monitor the exhaust gas temperature under normal circumstances, the new boiler is generally lower exhaust gas temperature, with the increase in run time will gradually increase. If it is found that the change is too large and exceeds 20 ℃ (algebraic difference), you should select the appropriate cleaning shutdown time. If this phenomenon occurs very frequently, it will have to check whether the normal combustion system. The oil pressure is too low, resulting in poor atomization low oil temperature, oil or wind than not, resulting in poor fuel air mixture so that the char combustion analysis hypoxia. Further, the dry back boiler, if the exhaust gas temperature increased abruptly, it is possible to return in a compartment between the second and third after the smoke box backhaul firewall leak smoke, shutdown would need repair.
On the following safety rules for oil or gas boiler from Henan fast boiler manufacturers of small series to tell you about the maintenance of the fuel gas-fired boiler. Servicing fuel gas-fired boiler can be divided into quarterly and annual maintenance service. Maintenance quarter (1) wash pump inlet filter and oil filter screen. (2) Check the pump packing and the like. (3) open manhole, hand hole cleaning boilers, internal inspection of boiler fouling and corrosion conditions, to determine the treatment and determine the need for periodic regeneration chemical cleaning. (4) washing water level gauge, three-way stopcock, etc., to check for leakage situation. (5) whether the control box to check that the circuit portion is loose, and clean fouling. (6) Check that all valves are good, and the cleaning operation. (7) on the rotating part of the machine once the lubricating oil is added or oil change. In maintenance (1) to open the fire door before and after the smoke box, check the gasket and soot corroded to decide whether to replace and clean up. (2) when opening the front smoke box, check the burners burner is burned, so that update. (3) check the corrosion of water and sewage pipes and the like. An insulating case (4) Check the electrical, electronics, circuitry, cables. (5) Check the electrical meter box of each instrument, buttons, pressure gauge accuracy.
As a leader in the fast side condensing gas boiler, in recent years, provide a clean boiler to Beijing multiple office units, was well received. I units through the preliminary investigation and contrast, select fast boiler, it turns out, party fast product does have quite a good cleaning environmental performance, in line with the Beijing municipal government requirements for air pollution emissions, the use of very at ease. --customer feedback