the energy-efficient gas boiler steam machine
Electric steam the energy-efficient boiler steam machine to be taken by each of the cathodic protection measures components of the electric steam boiler is made of different materials. In order to prevent galvanic corrosion, cathodic protection measures must be taken. Sewage treatment electric steam boilers. Bottom electric steam boiler blowdown can prevent flue gas condensation. Since the flue gas is flue gas condensation (diesel or natural gas) and the flue gas temperature in the aqueous too low, water generated. A portion of the moisture is discharged from the chimney, the chimney wall is absorbed, the rest is deposited on the bottom of the chimney. Water produced by the following factors influence: flue gas temperature (efficiency 91%, the flue gas must be at a temperature of 170 ℃) where the total surface area heat chimney, chimney and chimney material. Maintenance of the burner. Electric steam boiler and burner maintenance, repair after steam supply. Because the products of combustion will corrode the boiler, clean up carbon deposits, therefore, not allow the products of combustion in the boiler memory stay too long. We first opened when an electric steam boiler burner door, the rear housing panel removed, unscrew the screws electric steam boiler cleaning the rear opening. Clean fuel gas piping with a wire brush. With a soft brush to clean the combustion chamber. Electric steam boiler to remove residue in the boiler, the cleaning opening is screwed on the screw, closing the burner door seal check is complete. If electric steam boilers installed in areas where temperatures below 0 ℃ must take the following precautions: If electric steam boiler room outside, the room temperature drops below 15 ℃ or 18 ℃, the electric steam boiler running all day long. If no one in the room for a long time, the water should be emptied in electric steam boilers.
As to 10 ton LPG gas fired the energy-efficient boiler steam machine, here “10 ton” does not means the weight of this boiler, it means the boiler steam capacity per hour. Some clients may doubt the boiler only can burn LPG gas. Well, the writer reminds you this WNS series boiler can burn diesel oil, heavy oil, light oil, natural gas and so on. But this is designed to burn lpg gas, which means this boiler thermal efficiency can reach into highest level when burning lpg gas.
Our hotel attaches great importance to environmental protection philosophy, always bear in mind the protection of environmental quality in Xiamen. Therefore, we chose to stay ahead of the fast the energy-efficient boiler steam machine industry cooperation in clean and green boiler, electric steam boilers party fast to ensure that we provide the normal work requirements at the same time, has a very clear environmental performance. --customer feedback
Henan newly installed gas the energy-efficient boiler steam machine 1 what kind of work before starting. Henan newly installed gas boiler before starting what should be done? These include: the tightness of (1) hydrostatic test (overpressure test), test pressure member. (2) Trial and various auxiliary electric door damper check. (3) oven. Water inside wall of the furnace and gas water boiler tubes Henan removed. (4) cooking stove and pickling. Remove grease deposits in the evaporator heating surface system, rust, oxide scale and corrosion products, and other like with lye and acid. (5) furnace aerodynamic field test. (6) flushing pipe. Henan boiler with gas flushing a self-generated steam, the second steam duct heteroaryl residue. (7) check security doors. 2. Henan gas boiler before start time and temperature of water on what regulations? why? Water speed before the start of Henan gas boiler should not be excessive, winter generally less than 4h, other seasons 2 ~ 3h, especially in the beginning of the water should be slow. Cold boiler water temperature is generally not more than 100 ℃, so that the temperature difference between the feedwater entering the drum drum wall temperature is not more than 40 ℃. Henan not completely cooled gas boiler drum water temperature, mutatis mutandis, wall temperatures, generally the difference should be controlled within 40 ℃, it should slow down or speed water. The reasons are: (1) Since the thick-walled drum, slow expansion, the wall of the tube is connected to the drum wall is thin, expanded rapidly. If the inlet water temperature is too high or too fast, uneven expansion will cause the weld cracks occur, resulting in damage to the equipment. (2) when the water supply enters the drum, the drum is always in contact with the first half wall, if the water temperature and the drum wall temperature difference is too large, the influent fast speed, on the drum, the lower wall, the inner and outer wall inter will have a greater expansion difference, caused a large drum to additional stress, causing deformation of the drum, when severe cracks.