merchant gas water boiler system
In recent years, Hebei Province People's Government to respond positively to Blue Sky Battle action plan promulgated by the state, and all of 35t / h coal-fired boiler and below in the Hebei province out of the transformation process. First Hospital of Baoding respond positively to the call of the provincial government, eliminate serious pollution of the original coal-fired boiler hospital, citing energy saving steam boiler to natural gas as raw material. After a series of market research, WNS Series Split hospital condensing gas boiler boiler other fast soft spot.
Henan oil-fired boiler Introduction Product Introduction: Henan oil-fired boiler to run than electric heating boiler economic, easy to use than gas-fired boiler. With economic development and social progress and the improvement of people's awareness of environmental protection, coal-fired boilers due to serious pollution, moving away from sight, replaced by a new environmentally friendly digital boiler, such as electric heating boiler, oil boiler, gas boiler, electric heating boiler is more expensive, gas-fired boilers need to open a gas pipeline, then, if there is no gas pipeline, and hope boiler low operating costs, only select oil-fired boiler. Boot check: 1, various instruments, whether the instrument to confirm the adequacy of fuel tank, and the inlet valve is opened. 2, confirm the soft capacity and the water tank boiler water quality meets the requirements of the main valve is opened and boiler feed water inlet valve. 3, rotation of the oil filter to remove debris. 4, drain the remaining water in the boiler, while the opening operation of the low level alarm and chain. Features: 1, inserted within a fire retardant spoiler tube, slow speed exhaust enhance heat transfer, the temperature of the flue gas discharged from a low smoke chamber, reducing heat loss and save fuel. 2, furnace by computer-aided design, each of the heating surface is optimized, compact and reasonable arrangement, small boiler area, high thermal efficiency. 3, the user can set the start, shutdown time, after setting, no special duty, easy, and effort. 4, according to the boiler pressure furnace design, furnace provided with a top opening to atmosphere, the boiler is in an unpressurised state, there is no risk of explosion. 5, the inner fire tube inserted spoiler retardant, smoke slow speed, to strengthen the heat exchanger, combustion heat is conducted to a large extent in water, the discharged flue gas temperature is low smoke chamber, reducing heat loss and save fuel. 6, the water level sensor water level real-time monitoring, to continuously monitor the water level is normal furnace. While controlling the temperature and replenishment level sensor solenoid valves, the boiler water may be continuously supplied. 7, merchant water boiler system fuel water speed, water volume, widely used in factories, hospitals, schools, etc. required a large amount of boiling water units. Shutdown procedure: 1, when it is desired to deactivate the combustion boiler to the switch in the OFF position, the oil supply is stopped, the flame is extinguished, but the fan is still operating to blow away the residual flue gas in the furnace. 2, when the blower is stopped, the operation OFF switch to turn off the power and then, after closing the steam valve, and the fuel supply valve to close the valve. 3, open the drain valve when the discharge pressure is reduced after the boiler play an open valve, to drain the water in the boiler, and the steam partial open the drain valve to drain the water in the drum segregation. Daily checks: 1, check the water level regulator function: whether the automatic water pump stops. 2. Check flame monitoring. 3, is rotated, the slide cam portion lubricating, and wiping. 4, the flushing water level gauge 1-2 times (class), according to the proper operation, so that until the rinse water level gauge. 5, sewerage 1-2 times (class).
Performance horizontal oil-fired boiler is now full of water and the handling of horizontal steam boiler steam boiler accident refers to a horizontal design, in accordance with the fuel divided into horizontal electric steam boilers, horizontal steam boiler fuel, gas steam boiler and lying horizontal coal-fired steam boilers. Horizontal steam boiler flue gas flow due to the long, slow smoke, high thermal efficiency, it is very energy efficient. Horizontal steam boiler filled with water treatment and now the performance of an accident, the phenomenon of (1) the water level is higher than the maximum permitted cable, or can not see the water level, water table within a glass tube (board) Color dark boiler full of water. (2) all of the water phase as a color level gauge indication color. High-water alarm signal (3) water level alarm occurs. (4) decreased superheated steam temperature. (5) water flow is not normally greater than the steam flow. (6) water in a large number of sub-cylinder, severe trap operation. (7) with a large amount of water steam severe, increased salinity, water hammer occurs in the sound of the steam pipe, the steam connection flange outwardly dripping take place. 2, boiler full of water treatment rinse water table, determined to be minor or serious full of water full of water. Method: Close water table, the water pipe connected cock, then open drain cocks As can be seen from the decreased water level, indicating a slight full of water, the water supply is stopped, the drain valve open, put to the normal water level. Such as severe filled with water due to take emergency shutdown measures.
The reason the gas boiler burner noise analysis increases in the use of gas-fired boiler, found a small fire is normal, but when it becomes a fire goes out or flashing instability. First, because of excessive wind fire damper is provided; secondly, because of the fire valve microswitch (outermost damper group) is set incorrectly (fire damper is set larger than the amount of wind). Fuel circuit closing valve or port into the oil shortage, an oil filter plugging, increased gas burner boiler noise; Alternatively, since the oil inlet temperature is low, the viscosity is too high, the oil feed pump temperature, pump failure, fan motor bearing damage, and because the fan impeller dirty equipment, resulting in noisy equipment. Gas boiler in the course of the above failures, the viscosity is too high to spray the oil (heavy oil), and improper nozzle plate from the cyclone, and the like due to worn or dirty nozzles plus reasons. May be due to too high a heating temperature of the tank, leading to the steam delivery oil pump is not smooth; or because the fuel oil boiler caused by the water content. In use the gas boiler, the above failures should be gradually reduced, the heating temperature, to adjust the distance (0 ~ 10mm), cleaning or replacement should be about 50 ℃, the heating temperature should be raised. Oil change or drainage.