oil and gas fired one ton steam boiler
Fast Boiler Co., Ltd. is a really truly think about your clients practical solutions to business problems, this recommendation after this water-tube boilers put into use, the quality inspection departments, the nitrogen oxide emissions, soot and other indicators They are in line with national standards, but also very full of fuel combustion, high thermal efficiency, saves us a lot of fuel costs. This cooperation, I am very satisfied. --customer feedback
Gas-fired oil and fired one ton steam boilers can be cleaned during cleaning using efficient and environmentally friendly non-corrosive detergents. This will cause the tube to expose the primary color of the metal and reduce the impact of dirt and bio-algal sludge. After ignition of gas-fired steam boiler, attention should be paid to observing the furnace temperature and the temperature of the main steam. With the increase of main steam pressure, the flue gas temperature of boiler is obviously increased after ignition. If the temperature does not rise, you should go to the scene immediately to inspect the oil gun fire. The scale thermal conductivity of a gas-fired steam boiler is only 1/10 of that of steel. This hinders heat transfer when it scales on a heated surface. In order to keep the boiler in use The output shall increase the temperature on the combustion side. The increase of outlet temperature of gas-fired steam boiler increases the loss of gas-fired steam boiler, and the scale on the water wall of equipment will effectively reduce the heat transfer effect, which may lead to the increase of the temperature of water wall and the burst of water wall. When a gas-fired steam boiler is in operation, a series of chemical and physical reactions will occur in the furnace. In use, it will effectively form a hard and dense scale on the heated surface, which will directly lead to its heat exchange. The reduced efficiency and corrosion due to scale will reduce the heat absorption of gas-fired boilers.
Gas boiler safe operating procedures: gas-fired boilers this kitchen I believe we are not unfamiliar fishes it. But this thing is not so easy, and sometimes improper operation causing very serious consequences, so the gas boiler rules is very important. That in the end this is how the specific operation of it, if you want to know, quickly told us with a look. 1. All personnel must be familiar with the operation of the boiler performance and safety knowledge of the boiler operating certificates. This post is strictly prohibited non-operating personnel. Duty should be strictly in accordance with the operating records and do a good job shift recording, the security situation and the device should shift change operation tests, carried out. When the shift to check the boiler is intact. 2. Boilers and safety accessories should be inspected, and in the period. 3. Kai blast furnace gas furnace ready ① Check if the gas pressure is normal, not too high or too low, open the door of oil and gas supply section; ② Check whether the pump Sheung Shui, or opening the purge valve, until the Sheung Shui so far. Open the Water Supply System for each section of the door (front door section Sheung including pumps and boilers); ③ check level gauge, the water level should be in the normal position, the water level gauge, a water level required color plug in the open position, the water level to prevent false, if water can be manually Sheung; ④ check valves on the pressure pipe, must be opened, the wind deflector must all flue opening; each knob ⑤ checks the control cabinet are in their normal position; ⑥ oil and fired one ton steam boiler check valve should be in the closed state hot water boiler circulating pump outlet valve should be turned off; ⑦ checking water softening equipment is operating properly, a variety of indicators to create a soft water meets national standards. Open the power ⑴; ⑵ startup burner; ⑶ purge valve on the drum, is completely out of steam, the off; ⑷ inspection hole into the boiler, and the hand hole flange valves, the leak was found to be fastened, tight as the solid leakage maintenance shutdown; ⑸ pressure rise when 0.05 ~ 0.1MPA, replenishment, sewage, water supply systems and sewage screening test device while flushing water table; ⑹ when the pressure was raised to 0.1 ~ 0.15MPA, flushing pressure gauge trap; ⑺ when the pressure was raised to 0.3MPA, "fire load / small fire" knob to "fire" to strengthen the combustion; ⑻ when the pressure was raised to 2/3 of the operating pressure, start warming air supply tube, slowly open the main steam valve, to avoid water hammer; ⑼ drain valve is completely closed out of steam; ⑽ after all the drain valve closed, slowly open the main valve to open, and then half a turn; ⑾ "burner control" knob to " Auto "; ⑿ level adjustment: adjusting the water level (to manually start and stop the pump) according to a load, low load level should be slightly higher than the normal level, high load level should be slightly lower than the normal level; ⒀ steam pressure adjustment: adjusted according to a load combustion (manual adjustment Fire / small fire) ⒁ combustion state determination, determines the amount of fuel atomization air ⒂ observation condition exhaust gas temperature, smoke, temperature control is generally between 220--250 ℃ The flame color, smoke color, while observing the chimney exhaust gas temperature , concentration, adjusted to the optimum combustion state. ⑴ Open the power; ⑵ start the circulation pump; ⑶ slow circulation pump outlet valve; ⑷ startup burner; ⑸15 min "" Load fire / small fire "bit color button is turned to" fire "" ⑹ "burner control" knob spin to "automatic." 5A normal shutdown: hot water boiler ① "fire load / small fire" knob to "small fire"; ② off the burner; ③ close the fuel supply valve; ④ ⑤ closing dampers boiler after the temperature dropped to 50 ℃ , the circulation pump outlet valve closed. ⑥ stop circulation pump
There are two series of 15 tons of oil and gas boilers produced by ZBG. These two boilers are environmentally friendly packaging boilers carefully developed by ZBG. Many customers pay more attention to the price of the boiler, and the type and specific parameters of the oil and gas boiler will have a great impact on the price of the boiler. To know the price of a 15 ton oil and gas oil and fired one ton steam boiler, you need to have a general understanding of some specific information about the boiler.