1t concerning complete steam boiler
Finally, the delegation went into the manufacturing plant, the robot welding expressed strong interest in the robot field operations after watching the situation, I am using for manufacturing more refined variety of highly intelligent boiler equipment expression of praise. Mr. Liu is also the site to watch the robot control platform, careful observation stations located at the edge of the station systems. Side of photography Henan Daily reporter Chen Hui spoke to the tour group members in the field, this robot is currently in the province is a "little red network", has been the provincial media repeatedly reported.
Method: 1, first, the pickling operation is started, the boiler economizer, in addition to filling the drum with brine and water wall. 2, the ignition operation of the boiler, the boiler when the temperature rises to 70-80 deg.] C, the boiler flame, pickling may be performed thereafter. Before pickling, but also with superheater backfilling demineralized water, until the water until the overflow into the drum, to prevent the acid or acid-introduced into the superheater steam damage. 3, when the acid charged to the boiler, in any case, should not be firing boiler. Drum discharge hole and the other should be opened to discharge the generated acid and iron reaction of hydrogen, hydrogen has dissipated before sure to avoid the use of open flame or electrical sparking device to avoid risk of explosion of hydrogen. 4, finally, after the completion of filling the acid, so that the boiler economizer and soaked in the solution for about 6 hours, and then the acid is discharged, and rinsed with demineralized water superheater. Acid discharged after the acid drained, operating boiler feed pump, a water economizer capacity charged boiler feed water shut-off valve to prevent leakage.
Traditional coal-fired boilers inefficient and highly polluting; high fuel boiler operating costs, but also by pipeline constraints, the cost is too high; gas-fired boiler using natural gas as a clean fuel, soot content itself has very little, or even negligible, excellent environmental performance, loved and recognized by many enterprises and government departments.
When choosing a gas boiler manufacturers of what should be the standard? Want to make good quality gas boiler, first you need to select a good manufacturer, only one manufacturer has enough advantages, will make the product quality is guaranteed. When Hui user selection of such manufacturers, naturally, need to have their own standards, so when this choice of manufacturers, should be on what standard? First you need to see what kind of scale of the manufacturers standards. Among the industries, there will be a big difference in scale between the manufacturers and the manufacturers, manufacturers may be able to carry out small-scale production, but in no way on the strength of large manufacturers and compared.