industrial heavy oil fired water boilers in oceania
During installation, the technical team fast boiler plant according to the specific needs of our environment, our rational arrangement of stacks, pipes, and other auxiliary equipment, let us bring a lot of convenience in the latter part of the course. Fang fast responsible attitude also gives us impressed, sent a technical team for installation, commissioning and training to us, let us rest assured, peace of mind, peace of mind. --customer feedback
Hot industrial fired water boilers in oceania belongs to special equipment, and is also a kind of high temperature and high pressure thermal energy equipment. It is inevitable that some faults will occur in the process of operation, which are normal, but it is very likely that the explosion of hot water boiler will occur if it is not properly dealt with. Therefore, for equipment safety and personal safety, we must understand some prevention hot water boiler explosion common sense. In the design of hot water boiler, thermal calculation and strength calculation should be carried out strictly according to the requirement, the structure layout should be reasonable, and the material selection should be qualified. In order to ensure the boiler quality conforms to the drawing, the boiler should be constructed according to the drawing. The degree of delimitation. Boiler safety accessories should be complete, agile and reliable, and on-time maintenance, frequent inspection, failure of accessories should be replaced in a timely manner. Repair and repair the boiler inside and outside the boiler according to the schedule, repair and reform the existing problems in time to ensure the quality of inspection. 2. Fuel oil and gas-fired hot water boiler explosion accident in furnace to prevent explosion of hot water boiler should be carefully checked before the point of the hot water boiler, whether the oil path is tight (leakage), the pressure is normal or not, and the newly installed and modified oil and gas pipelines must be blown clean. Check whether the blower has been ventilated for 5 minutes before ignition, and analyze the reasons after ignition failure, and then follow the ignition procedure to penetrate the air. Ignite. For boilers that have not been certified for boiler use and annual inspection, the grater has the right to refuse to light the furnace. The enterprise should lay down the experienced stoves who have rich experience in the operation of the furnace. The staff of the furnace should step up the tour inspection, deal with the problems in time, prevent the flameout, and stop the fuel as soon as it is found out. The boiler shall be equipped with automatic protection devices, including automatic ignition, flameout protection, automatic combustion regulation and necessary interlocking alarm protection devices.
Boiler and burner What is the difference? Simply put by the boiler and boiler furnace consisting Pot is the place to absorb heat, increasing the temperature is generally endothermic water, or water absorbs heat of vaporization of components, mainly heating water wall, etc. surface composition, and the fuel is coal furnace, where the heat released by burning oil, material, and other components mainly furnace while the burner is to provide a combustion apparatus of the release of energy, the material is spray combustion, combustion air.
How to maintain steam boiler 1, when maintaining boiler, must cut off the power supply, must release pressure. 2, burners should be removed from boiler body every two months, and other foreign bodies such as carbon deposit and dust should be removed seriously. The photo-electric tube is polished once a month. The fuel filter should always be cleaned and filtered. Carefully clean the inner filter screen of the oil pump and do not destroy the gasket. The burner shall not run without oil to prevent damage to the oil pump. 3, the water level gauge shall be kept clean at all times and rinsed once a day by opening the cleaning valve to ensure the water level is clear. 4. The safety valve shall be pulled once a day in case of rust failure. 5, When the steam boiler stops running for a long time The power supply should be cut off and the maintenance work should be done: (1) dry maintenance, discharging the furnace water after the furnace is stopped, rinsing away the dirt in the furnace, drying the pot with a small burner fire (the burning time should not be too long, so as not to damage the boiler), Then, after all the boiler gas has been discharged, all pipe valves will be closed and checked every three months. (2), wet maintenance shall be applied to boilers with a period not exceeding one month, and the boiler water will be discharged after the shutdown, and the clean and full water will be discharged. Cut off the power supply and close the valve.