light oil burner industrial boiler use
During installation, the technical team fast burner industrial boiler use plant according to the specific needs of our environment, our rational arrangement of stacks, pipes, and other auxiliary equipment, let us bring a lot of convenience in the latter part of the course. Fang fast responsible attitude also gives us impressed, sent a technical team for installation, commissioning and training to us, let us rest assured, peace of mind, peace of mind. --customer feedback
The technical features of the wns series of oil and gas burner industrial boiler uses produced by ZG boiler, such as the design of large-volume combustion chambers, and the use of fully automatic low-nitrogen burners + flue gas recirculation system (FGR) systems to achieve ultra-low nitrogen emissions make this boiler The world stage is full of brilliance.
Now on the market most of the burner industrial boiler uses to gas, oil, biomass, electricity as the main fuel, coal-fired boilers because of its harmful pollution levels gradually been changed or replaced. In general, no boiler explosion during normal operation, but if it is due to the improper operation of the ignition or operation, it may cause the furnace or tail or secondary combustion flue explosion, resulting in serious danger of impact. In this case the role of "explosion vent" is manifested when the furnace or flue trace knocking occurs, the pressure within the furnace is gradually increased, when a certain value is higher than the pressure relief device can turn on itself through the explosion vent to avoid the risk expansion to ensure the overall safety of boiler and furnace wall, more importantly, it is to protect the safety of the boiler operator. Currently there are blasting boiler membrane and two kinds of swing-proof door.
The reason the gas burner industrial boiler use burner increased noise analysis when making use of the gas boiler and found this small fire normal, but this time turn the fire, extinguished or flashing instability. First speaking, that is because of this fire damper of the air volume setting is too large; i.e. after an oil fire because the micro-switch valve (damper outermost that group) inappropriate setting (set lower than the fire damper of the air flow larger) burner gas noise increases, mostly because the oil shut-off valve which is closed or lack of oil into the oil filter clogging; or, this is because of low temperature into the oil, the viscosity is too high or the pump into the oil temperature is too high; oil pump failure; fan motor bearing damage; there is because the fan impeller dirty equipment resulting in large noise. The above-described failure when using gas boiler, but also because the viscosity is too high oleaginous easy to be atomized (heavy oil); cyclones and because improper disc and the nozzle pitch; Note that because the fire is worn or dirty nipple; also because this preparatory tank the heating temperature is too high, causing the oil pump oil feed steam does not conform; or because the fuel inside the boiler resulting aqueous oil. When the above-described fault gas boiler used to perform this process, the test should be done gradually decreases; after heating temperature should be; adjusting the distance (between 0 ~ 10mm); clean or replace; is set to about 50 deg.] C to about; or drain oil change.