horizontal structure boiler machine
ZG series 20 ton circulating fluidized bed horizontal structure boiler machine fuels include coals, lignites, biomasses, refinery by-products, slurries, etc, When fuel quality and range are critical to your project’s viability you can depend on our advanced Circulating Fluidised Bed (CFB) boiler technology. Constant refinement and innovation means you benefit from a product which can deliver the critical reliability and environmental performance you need.
How to maintain water supply and horizontal structure boiler machine water of Fangkuai boiler during operation the quality of water supply and furnace water of Fangkuai boiler should meet the requirements of GB/T1576-2008 (Industrial Boiler Water quality). And sample and test regularly. The quantity and frequency of the discharge shall be determined by the laboratory personnel. Test and discharge shall be recorded in detail. 2 Monitoring of rotating machinery shall be carried out by means of one look, two ears and three touches for pumps, fans, pumps, etc. The discovery of anomalies, that is, take measures to deal with. If necessary, the furnace should be shut down and overhauled, but it should not be careless. The oil level of the tank on the 3rd day If there is no automatic control device for oil level, the oil level should be checked regularly and it is found that the oil level is too low to be used for 2 hours. Please inform the fuel personnel in advance of the injection of new fuel. 4 the water level control of the soft water tank is generally used to automatically control the operation status of the 5 water treatment equipment to check periodically for the failure of ion exchangers in the water treatment equipment. Under normal conditions, the exhaust temperature of the new Fangkuai boiler is generally low, and will gradually increase with the increase of the running time. If it is found that the change is too large and exceeds 20 ℃, the appropriate time to shut down the furnace and clean the ash should be chosen. Such phenomena as If it happens frequently, check that the combustion system is normal. If the oil pressure is too low, the oil temperature is too low to atomize bad, or the air-oil ratio is not correct, resulting in bad oil-gas mixture, resulting in anoxic combustion and carbon precipitation. In addition, for dry-backed boilers, if the exhaust temperature increases abruptly, it is possible to leak smoke from the fire-proof wall between the second and the third return of the rear chamber, which needs to be repaired.
2. Expert firing system with high efficiency cyclone
3. Improved boiler efficiency up to 90% and advanced desulfurization process
Recently, Taiyuan, Shanxi Province Environmental Protection Leading Group issued a circular on promoting the transformation of ultra-low emissions and low nitrogen transformation of biomass horizontal structure boiler machines gas-fired boiler. Resolutely implement - the latest requirements "2018 in Beijing, Tianjin and the surrounding areas in 2019 autumn and winter tackling air pollution comprehensive management action plan" in, and further reduces boiler emissions standards.
1, 2019 until October 31, the use of boiler tail decoration efficient dust removal, desulfurization, stock device is accomplished ultra-low emission biomass boilers transformation of the necessary funds by the counties (cities, districts) and users together to solve, not the municipal finance I grant.
2, October 31, 2019 update for ultra-low emissions of nitrogen gas boilers, electric boilers biomass boilers, municipal finance one-time grant 30 yuan / square meter construction costs, in part by the lack of counties (cities, districts) and user common solutions.
Way: by transformation to replace the low NOx combustion, a flue gas recirculation device installation mode, NOx emission is less than 30 mg / m item.
NOx emission cuts ≥50%, and the concentration value of less than 30 mg / cubic meter project, to give up prize money of 30% in accordance with the transformation of investment.
3, after December 31, 2017 the new gas boiler, should meet the emission requirements on Taiyuan low NOx combustion, but does not enjoy the low NOx combustion subsidies.