high temperature lry oil burning hot water boiler
How to select energy saving, gas-fired? We have to look at or listen to illustrate the introduction of natural gas boiler technician in the procurement of natural gas boilers. Gas-fired steam boiler, the type of gas high temperature lry burning hot water boiler, gas conducting oil furnace, boiler different for different occasions. After determining the procurement of natural gas boiler models, need to understand the specific configuration of the boiler, configure the following criteria: 1, the main boiler is equipped with auxiliary equipment and what. 2, meters, valves and water boilers require careful examination to understand. 3, understand the control system of the boiler: boiler power electrical cabinets, power boiler control switchgear. 4, check the electrical control cabinet, console, the control system, the drive, a display, and other electrical equipment. 5, and riot unit boiler tank daily inspection. 6, boiler factory testing and commissioning. Clear cost price of natural gas boilers, installation cost of materials and installation of boiler worker costs, transportation costs and other parts.
Oil-fired boiler fuel boiler fire safety regulations and environmental protection is certainly more convenient than traditional boiler, the oil but because of the special nature of their fire protection system is indispensable, its fire are: 1, tank farms, offloading pipes should have a reliable anti-static safety ground, and tested periodically grounding resistance value (less than 0.5 ohms). 2, prohibits storage of flammable oil region, inflammable and other temporary buildings should be promptly removed. 3, prohibit or stop operation standby state of an oil pipeline welding work. When the welding work must be carried out in oil pipes, oil pipes oil system before welding, the welding operation will need to be running or stopped off standby state (e.g. oil pipe welding or detached house blocking plate), and then the oil segment flush pipe, to ensure that no internal oil and gas, oil and gas welding operation in order to prevent knocking. 4, the internal oil zone fire operations, must apply for work ticket flare, and should have reliable safety measures 5, to strictly enforce the oil zone management systems. 6, foam fire extinguishing systems and equipment, oil fired boiler systems must be checked periodically tested as required. 7, hose fuel system should be checked regularly replaced. Since the hose to prevent fuel leakage caused by aging. 8, when the inspection of oil leakage found when the insulation material, should eliminate leakage point, and replace the insulation material. 9, note that the monitoring oil tank, when the oil temperature exceeds 50 ℃ when shower water into the tank. Fire Code is more than oil-fired boiler, and I hope we strictly observed for their own safety.
Cooperation with the fast boiler really is a very correct decision of our hospital. The party quickly boiler shell not only provides us with high-quality and high-performance energy saving boiler coexist; also provides free installation and post operation and maintenance personnel training services for our system, very caring, thoughtful. --customer feedback
Horizontal condensing pressure high temperature lry burning hot water boiler Precautions: 1. boiler control system to be used according to the instructions for correct operation. 2. boiler outfall road, drainage pipe must be connected to a sewage ditch. 3. The furnace room layout is reasonable, boiler room should always be kept dry and clean to prevent moisture control system. 4. types of fuel: natural gas, city gas, liquefied petroleum gas, light oil, heavy oil. The temperature should be in accordance with local diesel, heavy oil should be previously heated to 40 ~ 60oC. 6. Power Requirements: rated voltage AC.380V, 50Hz. Voltage fluctuations within the rated voltage range of ± 5%. Boiler installation should the installation protective earth wire. 7. Non placed around the boiler oil, gas and other flammable materials. Tank, the gas tank and the boiler room external wall footing line pitch should be more than 15 meters. When there is a specific reason to shorten the distance fire, it should be the local fire department and the relevant authorities; if using underground arrangement, the cover layer should be more than 0.5m, around the need to increase the firewall; underground, pumping anchor bolts must be tightened or other measures adopted to prevent the displacement of fritters. 8. Horizontal condensing pressure hot water boiler pipe PRECAUTIONS: