2017 new type natural gas hot water boiler
The importance of the power plant boiler control systems and boiler room design load Description: This important site for boiler products and key words, because it is inclusive of all of the Website, so, in order to help people to learn their work from different angles, below, the boiler will start from the whole to expand and be specific, in the form of learning, in the form of questions and answers will be used to ensure that everyone's learning. 1. boiler feed water and boiler feed water, these two are the same? Boiler feed water and boiler feed water the two, although the name, only a difference of a word, but they are not the same, because, boiler feed water refers to the water softener after chemically treated, and boiler feed water, which is from the chemical water workshop to between oxygen, and then through the feed pump into the economizer of soft water, which is in the process compared to the boiler feed water, but also increase oxygen and heating these two operations. So, to sum up, they are not the same. 2. The power plant boiler combustion control system in which it important? In the boiler power plant, it can be said, combustion control systems, it is very important to a system, because it is in the boiler master control system, therefore, will have this conclusion, therefore, on this issue, their answer Yes. Further, the configuration in which the main fuel is a control system, air flow control system and furnace pressure control system of the three parts. 3. coal, oil or gas boilers, boiler room that is, the need to build an independent?
The partnership, fast boiler for the user responsible attitude to have left a deep impression on our fireman boiler operation is not very skilled, fast deliberately sent a party of professional and technical personnel for our on-site supervision of installation, commissioning and training to ensure that the latter can operate our good boiler fireman. --customer feedback
The main problems of autonomous decentralized boiler heating mode: 1, "two small" boiler room that is small-scale (10,000 m- for the following boilers 60%), small boiler capacity (single boiler average capacity of only 2 tons / hour). "Two low", i.e. the boiler load is low, the thermal efficiency is low. Calculated heat index 70W / m =, 0.7KW (i.e. 1t / n) for 10000m =, in fact, only for 4000m =, less than half, in the "Mara car" low load operation. Thermal efficiency is naturally low, generally only reach 50-60% oC "two can" That is more than the energy consumption, the existing multi-intermittent heating (burning six hours every day and night, stopping six hours, repeated twice). In the current institutional heating intermittent heating accounted for 82%, only 18% of continuous heating. 2, boiler room hire older workers and the burning of a modern boiler during operation merely by virtue of the experience "the sky light a fire," there is no scientific basis for heating, that is, how many points you cold, warm day less burning point, which is very difficult to achieve the purpose of heating and energy requirements. 3, the heating system is unreasonable, due to some historical reasons causing heating in the system has inherent missing, and in the intermittent heating is due to habits die hard so the resulting decline in the quality of heating also a waste of energy. 4, which is related to the owners and the quality of that set out secretly put a hot water tank, can lead to heat loss, water loss occurs, really makes the heating unit is really a headache, which cause heating problems. 5, since the local heating technology of high and low level, so that in the heating process, the heating requirements for the simple pursuit of the distal end of the owner excessively coal temperature of the heating water, resulting in overheating proximal end, a distal end of the warm unbalance, or warm proximal distal cold conditions, which resulted in a waste of energy, will not help solve the problem. 6, the boiler disrepair, will take place at the junction of the pipeline corrosion, fouling and even the phenomenon is really due to the HVAC heating during water treatment errors caused by, resulting in fouling of the boiler heating surface, or Since the agent is such that the boiler ash surface to form grime, which is management problems. 7, the high heat load design makes enormous waste in financial resources, but also makes the device parameter selection is also too large, the most important thing is a waste of energy. 8, due to improper selection of the boiler supply pump, such that the heat medium low boiler room parameters, the performance of the boiler is low lift, low thermal conductivity, insufficient heating vicious circle. 9, due to the design of overkill situation arise, ie, a single heating boiler can solve the problem, but using a more common heating boiler, resulting in low thermal efficiency of large coal consumption and generate unreasonable conditions. 10 vertical imbalance, if indoor heating system will be conducive to eliminating the balance of water resistance, which requires the designer to identify line) inputs the number of circulating pump is too large, such a large pump flow, low return temperatures, generally in 25 degree. This will increase electricity consumption. 11, about the nature of different heating buildings, commercial buildings and residential buildings if the use of a heating system is the same, then since the days of the commercial building heating requirements of large, large civil construction heating at night, if you can not time-heating, is bound to cause waste of energy. 12, single-tube heating system installed can not be achieved thermostatic valve on the radiator, but now a lot of indoor heating systems or belong to single-tube system, which is not conducive to long-term development. 161, why gas hot water heating boiler heating problems occur each year to slow the heating time, a gas boiler heating the user of the problem in many areas of heating will slow, but the problem is often not the fault based on the boiler itself. In this regard, today we elaborate on the reasons for this phenomenon. 1, because the use of gas-fired boiler heating, after carrying out the heating boiler ignition, but also need to go through the oven, cool-running, heat exchangers and other process, so as to make heating gradually warming. After the gas 2017 new type hot water boiler heating during ignition, the oven is ready to work early each year heating must be carried out, a process that takes about 3-5 days to complete. 2, the use of the process, gas hot water boiler also need to go through the process of heat transfer, the temperature will gradually rise. Gas heating boiler heat exchange process is mainly water cycle process, stand out from the hot water not flow directly to the residents of the home heating network, but need heat exchanger unit to transfer heat energy in the hot water heating plant to the residents of the home in the circulating pipe network. 3, starting at the initial stage of the heating boiler, water temperatures of the respective heating stations is not very high, coupled with the complex structure of the network, the gas hot water boiler heating hot water heat exchanger is a process, especially in the end of the pipe network user, heat transfer process will be a little longer time.
Importance of continuous Feedwater equipment in Gas-fired Steam BoilerThere are two kinds of feed water methods for steam boiler, steam feed water and electric feed water. Steam water supply equipment mainly refers to water injector and steam reciprocating pump, usually acting as backup water supply equipment in boiler. Another commonly used electric feed-water method is through the electric centrifugal pump and vortex pump to feed the water. During the operation of steam boiler, the feed water equipment is usually required to have the active control function. The water level can be lowered to a certain azimuth to actively open the pump to feed the boiler, and the inlet water to a certain direction can also actively stop the pump. Hot water boilers can also be recycled according to in / out water temperature or heating conditions. So gas boilers are usually equipped Use an electric centrifugal pump or vortex pump instead of steam-powered feed-water equipment. The feed-water equipment in gas-fired steam boiler is a very important equipment in all boiler systems. It is responsible for supplying raw materials to steam boilers; allowing it to produce the steam it needs to be used. In the process of boiler operation, it is necessary for the water supply equipment to run synchronously so as to supply water to the boiler continuously, so that the boiler can get enough water supply to run normally and safely.