distributor appliance boiler system
Boiler plant equipment as three major important energy conversion device, fuel chemical energy into heat energy, and the pot was heated using thermal energy to become hot water having a sufficient quantity and a mass (steam temperature, steam pressure) steam turbine for use. The Anyang City, the power company to my company to buy a split 2 tons of steam condensing gas steam distributor appliance boiler system for supplying electricity demand. The WNS series split condensing boilers using advanced technology designed to greatly improve the thermal efficiency of the boiler, up to about 96%.
15 ton biomass steam distributor appliance boiler system in Peru
Peru has developed agriculture, high forest coverage and abundant biomass resources. Biomass boilers have a good market in this country. In Peru, there are many food processing companies that are very fond of using biomass steam boilers for enterprise production. Last year, CBM provided a 15-ton biomass steam boiler for a food factory in Peru.
What method of industrial distributor appliance boiler system feed water treatment for industrial boiler feed water treatment methods are what? Treatment agent tank features are: small (1) investment, low cost, easy operation; (2) a chemical treatment combined with the outer tank, may further eliminate residual hardness; (3) environmental pollution; (4) can not be completely prevent boiler scaling; (5) water hardness inappropriate. The main method of treatment of the pot are: 1) salt method. Commonly used is trisodium phosphate, sodium carbonate (sodium carbonate), and fire (sodium hydroxide), which is the most common soda. 2) Integrated scale inhibitor law. Sodium hydroxide, trisodium phosphate, sodium carbonate and tannin extract composition Comprehensive inhibitors. Potting, there are two methods: one is administered intermittently, is continuous administration of two kinds. 3) an outer pot chemical treatment. The use of auxiliary water treatment equipment, boiler water softener recharge to ensure that qualified and softened, desalinated water.
Two main cause corrosion of fuel gas-fired distributor appliance boiler system corrosion occurred after, not only the effective thickness of thin metal, and make the interior of the metal microstructure destruction, poor mechanical properties, resulting in pressure capacity of the fuel gas-fired boiler to reduce, shorten the service life, as well as early retirement. Some corrosion can cause damage to the equipment in the case of people unaware of serious accidents will happen when bad. Therefore, to find the cause of corrosion and thus effectively prevent the occurrence of corrosion is very important. 1. Flue gas fuel boiler fuel combustion corrosion, high temperature flue gas generated passes through condensing means, the flue gas water vapor dew encountered low temperature wall surface, the condensed water formed can severely erode the metal surface. 2. Lime scale can lead to corrosion of metal corrosion under the scale, the scale is deposited there under the conditions of scale from the hole, a slit pot water infiltration, rapid evaporation of the scale between the deposition layer and the inner heating surface of boiler boiler heating surface. In the scale layer, boiler water can be concentrated to a high concentration. Some of the material under conditions of high temperature and high concentrations of boiler heating surface will produce severe corrosion, such as NaOH and the like. Scaling, corrosion process mutual promotion, will soon result in damage to the metal heating surface, to cause the boiler tube rupture occurred.