th steam boilers quote
Hot water boiler does not use softened water, what harm? Hot water boiler does not use softened water, what harm? Boiler during operation of the water quality requirements are more stringent, thus making boiler feed water, will install water softening water treatment device, then, if not soften water What harm would it deal with? 1. waste fuel because the water is not timely treatment, over time, the water content of non-compliance with the boilers physical or chemical reaction, can cause damage to the boiler wall or boiler scaling, affecting boiler the thermal insulation effect and efficiency, and that, in order to ensure that this part of the loss, the amount of the fuel will increase with. 2. there will be corrosion. Since the acid-base substance and oxygen present in the water with the metal body of the boiler should chemical method, so that the furnace wall is gradually reduced, dents, reducing the strength of the boiler, can easily cause accidents operation. Of course there will be other hazards, such as boiler output, normal boiler water cycle, boiler shortened life expectancy and so on. These are the dangers of not using soft water changes caused. After analysis of the dangers of not boiler water softening treatment, you will find, if you want, such as the boiler low-power high efficiency, high operational safety, water softening boiler also make one of the most important factors, therefore, strictly according to the standard treatment also needs to be carefully done.
Steam is one of the major energy plants, due to the need of the production process, almost a project, practicing two steam engineering, molding, primary drying, and secondary drying and other production processes to be used in various heat exchangers and other steam. However, the boiler steam pressure needed food business decision process is based on actual customer production and processing products: such as fumigation stage, usually less than 1.6MPa rated steam pressure can be. However, as of now, boiler worked in more than 600 fast boiler used in the food industry, the existence of more specific food plant process use, but also the maximum design pressure of not more than 25 kg.
Shunde main business of special sea oil production and processing, etc., in the course of special oil refining, a large amount of steam required for oil and gas extraction, distillation and extraction technology and other aspects, therefore, the boiler is supplied special sea oil processing technology company Shunde indispensable less equipment. As environmental policy progresses, the chemical industry as more polluting industries are highly valued the various departments of quality supervision, sea Shunde companies to follow the development of the State Environmental Protection pace, choose clean the boiler industry-leading fast Boiler cooperation with the parties by quickly assess the specific needs on-site estimates and sea Shunde, to provide a SZS series of 25 tons of steam water tube th steam boilers quote (SZS25-2.0-YQ).
The installation of pressure gauges for Fangkuai boilers depends first on the pressure point and the space position of the pressure gauge (or pressure transmitter), and then on what pipeline accessories there are and how to lay them. (1) in order to measure the static pressure correctly, The extraction port must be perpendicular to the medium flow. No chamfering, flanges, and burrs. When measuring the liquid pressure, the pressure-taking port shall be drawn from the lower part of the pipe section, so as to prevent the gas in the liquid from entering the pressure-guiding line; When measuring the gas pressure, the pressure-taking port should be drawn from the top of the pipe section to prevent dust in the gas and water droplets from entering the pressure-guiding pipeline. (2) the inner diameter of the pressure-taking pipe is usually φ 7 / 1. 3mm (for water, steam), its length should not be too long (< 60m). If the diameter and length of the pressure-taking pipe are too small, the dynamic transmission of pressure measurement will be affected and the dynamic error will be increased. The inner diameter is too large, not easy to maintain and install. The pressure-taking line shall not be laid horizontally in order to prevent the accumulation of bubbles (when measuring the liquid) and the water column (when measuring the gas). (3) the pressure-taking line must be fitted with a needle-shaped valve (to cut off the pressure in the event of failure of the pressure-taking line in operation), Secondary needle valves (instrumentation, stop, replacement), condensing coil and elbows (isolation elastomers from high-temperature heating in the medium and easy to install sealing patches); and Sewerage valves and sewerage lines, etc. For special pressure measurement, the pressure taking line must also be equipped with vent valves, isolation rooms, etc. (4) the installation site of the pressure gauge (pressure transmitter) shall meet the environmental conditions (temperature, humidity, vibration, etc.) used by the instrument, At the same time, it should be easy to observe, repair and ensure safety. The pressure-taking pipeline of high-temperature medium must be coated with a thermal insulation layer to avoid scald when punching the tube.