boilers for fruit distillation
When gas boilers for fruit distillation ignition, need to pay attention to what matters is the primary determinant of the ignition gas boiler started to master boiler ignition precautions to ensure the safe and stable operation of the boiler. 1, for gas-fired boilers, the ignition time if not successful, the need to purge the furnace flue, before a second firing. 2, in order to prevent a gas explosion, gas boilers not only to purge the boiler furnace and flue gas channel before the start, the need for a purge gas supply pipes. The gas supply duct media typically purged with an inert gas (such as nitrogen, carbon dioxide, etc.), and the purge of the boiler furnace flue with a certain flow rate is the flow rate of air. Case 3, in the rear of the boiler did not take anti-corrosion measures or condensation water collection, etc., gas boilers should avoid long-term operation at low load or low-parameter case. 4, the combustion gas boiler adjustment process, to ensure the quality of the combustion, it is necessary to detect smoke components, to avoid too high excess air and incomplete combustion. Generally, the gas-fired boiler during operation, the carbon monoxide content should be less than 100 ppm, and at high load operation, the excess air ratio should not exceed 1.1 to 1.2; under low load conditions, the excess air ratio should not exceed 1.3.5 , real-time attention should fireman switch case of a gas valve. Gas line not leak, if unusual circumstances, such as the boiler room abnormal odor, not open burners, ventilation should be checked to exclude odor, check valves, only put into operation is determined normal. 6, a gas boiler for liquid fuel with air, special attention should be ventilated boiler room. Because of severe liquid gases than air, in case of a leak can easily cause condensation of liquid and spread on the ground, resulting in a vicious explosion. 7, after a period of time or inspection line outage, when the single-column hydraulic machine into operation again, should open the vent valve, bleed time, deflation time should be determined according to the length of the pipeline and the gas species. If a longer boiler downtime, it should cut off the gas supply valve, close air release valve. 8, the gas pressure is too low and not too high, to be run within the set range, the specific parameter provided by the boiler manufacturer. When the boiler running for some time, found that the gas pressure is below the set value, should contact the gas company. Burner operation for some time, should be checked line filter is clean, as a lot of pressure drop, there may be too many impurities in the gas, the filter is clogged, washing should be removed, if necessary, replace the filter. 9, should comply boiler unit boiler manufacturers operating instructions provided by the manufacturer and the burner, and the description should be placed in a convenient place for easy, for inspection. When there are unusual circumstances and can not solve the problem, depending on the nature of the problem promptly contact boiler plant or gas company, to conduct maintenance by a professional maintenance staff. 10, shall comply with the provisions of the relevant gas. Not free to fire the boiler room, prohibited welding, gas welding and other operations in the gas pipe roadside.
horizontal boilers for fruit distillations for pharmaceutical industry
CBM provide a whole services for pharmaceutical industrial horizontal boiler systems. Meeting the stringent sterility demands of the Pharmaceutical Industry.
Gas boilers for fruit distillation works and the principle of gas-fired boiler of a gas furnace gas fired boiler is also known, in general is natural gas, liquefied petroleum gas, city gas and other combustible fuel gas to heat utilization equipment, according to their functions can be divided into different type, such as a gas hot water boiler, gas hot water boiler, gas steam boilers, gas and other industrial boilers, gas boilers as China's coal-fired boilers have been banned since a new type of economic energy-saving products, it is widely used in the boiler civilian areas, mostly for heating and bath with. Here to share a gas boiler operating principle: the working principle of gas boiler and substantially conventional boiler is connected, is injected through the burner head of the burner into the furnace to ignite the combustible gas-mixed flame, so as to achieve furnace of the boiler, heating furnace tube, such as a good boiler Henan party shares fast production of gas boilers will be designed on the basis of these three return bend the combustion chamber or multi-backhaul goal is to deliver more local temperature, and because it is multi-cycle, high-temperature combustion smoke is produced after several times through the loop, the temperature in the discharge thoroughly complete transfer. The whole process is most important boiler with burner heads and fuel, together with the overall thermal efficiency of the superheater, the effective mating of these components reheater, economizer, an air preheater and the like to achieve the lifting of the boiler. These are the working principle of gas-fired boiler, where our customers want to buy gas boiler recommend a good product, Henan local production SZS series shares quick and efficient gas boiler, the product is currently one of the most advanced energy-saving equipment, 1 tons the gas boiler can save up to 10 cubic meters per hour of natural gas, it is a rare quality products. Consult Engineers Order online!
State all the more attention to environmental protection, to provide more excellent atmosphere, we respond positively to the country's environmental protection, promote the boilers for fruit distillation from coal to gas project. Among the many boiler suppliers, we chose the fast boiler. First, the party quickly done very well in terms of cleaning the boiler, the second is fast side also very comprehensive after-sales involved. The optional gas boiler was used after running fully meet the needs of our pharmaceutical production, both energy-saving and environmental protection, but also a very high thermal efficiency, saved us a lot of fuel costs. --customer feedback