natural gas boilers foreign
Gas-fired steam boilers foreign abnormal situation, how should we deal with it? When we use gas steam boiler, failure or abnormal phenomena it is inevitable, but in order not to affect the normal use, in the event of a problem gas steam boiler to be timely processing solutions, then the face of all kinds of circumstances, we should how to handle it? Share some of the ways we deal with unusual circumstances. If only gas steam boiler circulating pump abnormalities, such as its current decreases, the pump outlet pressure back to zero, which indicates no oil pump is idle, it may be caused by oil vaporization. Yang identify the reasons therefore first vaporized measures; such as clogging of the filter circulating pump bypass opening evacuated immediately clean the filter; heat transfer fluid as a result of added aqueous or decomposed gases are not excluded in the system, should immediately open the vent an exhaust valve. Circulation pump pressure constant, the current increases and the flow drops, deterioration of the thermally conductive fluid, the viscosity increased, should be replaced or regenerated. New heat transfer fluid as a result of decomposition of aqueous or excluded gases in the system, should immediately open the vent valve of the exhaust gas. When the current is lower than normal circulation pump, the circulation pump efficiency is decreased, the flow rate decline may be heating pipes plug fouling, stainless steel chain should be cleaned. If the gas steam boiler before and after the filter increased in pressure, the pump inlet pressure drops, the filter may be stuck, the opening of the bypass, disassemble and clean the filter. In addition to its low furnace outlet temperature liquid phase heat carrier, mainly for lack of heat fouling problems, it is timely soot blowing. Gas steam boiler grate more common problem is stuck, there are reasons including breaking grate or the grate off loose pins; coal grate has stuck to metallic inclusions; arched grate; slag is sinking the tip of the grate stuck. In response to this phenomenon, the required reverse hand grate plate debris removal, replacement breaking grate after the start, then jammed as startup, stop the rotation of the reasons detailed inspection to resolve. But also to re-adjust the adjustment screw on both sides of the grate tension, if still does not work, we need to replace the sprocket.
Burner assembly design choices boilers foreign burner already developed into a general burner, the burner mentioned three words we do know so the boiler burner and employment is related to fire, the fire more time in on helping us, but not only each careful it will become your enemy. ?? So how can you take advantage of warranty using the boiler burner for the moment is to use it and design staff at the time the design of the burner design it is regrettable that we take a look: for precision temperature conditions of the mobilization method the fishing gear, you may wish to use some fire in Sec manipulate manipulate fire, line by line, to mobilize the burner. If the use of heavy fuel oil atomization , Shen oil burner atomizer machine may corroboration fuel burner, the burner region F medium nebulizer, geographical differences in the situation, the situation includes a differential difference burner the viscosity of the condition to be employed. When the heat value of the gas used as the fuel gas pressure, as many thermal differential value of the types of gas, the pressure is not and will not, so the manufacturers want to use in a combustor using a fuel burner stated categories, the number of heat value, how poor the pressure to adopt appropriate burner to prevent the inaccurate use of crisis. Furnace temperature and pressure using burners, burner manufacturer's forced to declare himself set which type setting, the furnace pressure is low is still active, multi-poor pressure, temperature arrived tall. Given the furnace temperature category.
Still 8 cultural and creative industrial park is located in the Chaoyang District, Beijing, Bali Zhuang Chen Lin, No. 2, construction area of 493,300 square meters. Surrounded by quintessence of Court, Red Sandalwood Museum, Shanxi Museum and other famous attractions. Due to its special geographical location, has very stringent requirements for providing heat boilers foreign plants. Carefully selected to finalize cooperation with our company, signed a two He Lide series complete condensation pressure hot water boiler.
Gas boilers foreign heat loss through the combustion of fuel gas boiler, will release some heat, which will supply part of the user, some will be recycled and part is inadvertently wasted. So these are wasted heat lost through the ways in which it (1) heat losses:? Flue gas exhaust gas boiler part of the heat into the atmosphere, causing the boiler heat losses, it is each boiler term heat loss Dazhong biggest one. The main factors influencing the heat loss is higher exhaust gas temperature and the amount of smoke exhaust gas temperature, the greater the amount of smoke, the greater the heat loss. Low exhaust gas temperature depends mainly on the number and operating conditions of the heating surface; the amount depends on how much leakage exhaust case and the furnace excess air, flue. (2) heat loss incomplete combustion gas: a part of the unburned combustible gas is discharged with the flue gas to heat loss caused by heat in the flue gas. The main factors affecting the incomplete combustion gas heat loss is the excess air and furnace structure. Excess air coefficient is too small, uneven air is mixed with fuel, easy to generate carbon monoxide and other combustible gases; excess air coefficient is too large, the furnace temperature is lowered, the combustible gas is not easy ignition and combustion. Furnace volume is too small, combustible gases in the furnace too late to enter the combustion flue gases caused by incomplete combustion heat loss. (3) heat loss: the furnace heat loss, frameworks, pipes, door opening caused by heat dissipation to the surroundings. Size depends on the heat loss factors of the size of the surface area of the furnace gas steam boiler, heat insulating properties and thickness, the outside air temperature and the flow velocity. Electric heating reactor common external damage: an electrically heated reactor despite external corrosion has a high etching resistance against acid and alkali resistance, but our electrical heating by the heating apparatus is a kettle layer and an outer tire iron constituted. Such a medium is iron acids and bases are not corrosion-resistant. If we would have the production process if the reactor cover or screwed pipe joints without seal failure or leak acid tire iron reactor apparatus for electrically heating the outer corrosion. Corrosion support member 2. The reactor was heated electrically heated reactor during installation, support or other support member may be mounted directly on the floor, due to the long manufacturing operations on the floor may be deposited with corrosive media, so that for support our reactor electrically heated apparatus corrosion, resulting in the supporting force of each of the support produces a change resulting in a change in stress in the damage produced during heating layer. 3. The electrically heated reactor stress spout in the electrically heated reactor, when the steel of the pipe and the pipe joint, since the thermal deformation and the reaction was heated electrically heated autoclave vessel or duct stressed cold might damage the pipe.